Reversing Valve Coil - Troubleshooting
If 24 volts is present at the coil, the coil is probably bad. However, it should still be tested.
- Remove the screw that holds the coil onto the shaft.
- Slide the coil off of the shaft and unplug it from the wire.
- Set meter to ohms and test coil.
- Resistance should read between 13 to 16 ohms.
- Reversing Valve: A device in a heat pump that reverses the flow of refrigerant as the system is switched from cooling to heating.